Sewer Service Requirements
For complete information, see City Standard Specifications Section 3.
A separate sanitary sewer service must be provided to each lot.
A sewer backwater valve is required on a sewer service if the lowest floor elevation is lower than the elevation of the upstream sewer manhole lid nearest the site, or if high sewer main velocities may create above normal air pressure within the main.
Sewer Service Pretreatment
Developer required to submit sanitary sewer pre-treatment device plans, specifications and/or any other pertinent information relating to pre-treatment facilities, for approval to the City's Municipal Services Department.
Pretreatment devices - to be installed on sewer service as required by KMC 14.22.020 (d) or demonstrate that sewer discharge will not exceed effluent quality requirements of the chapter.
Restaurant & Food Preparation Facilities
The City requires restaurant and food preparation facilities to have an outside grease interceptor in accordance with the Uniform Plumbing Code (WAC 51-46) Appendix H. The location of the interceptor will be approved by the City Municipal Services Department for inspection access requirements. The sewer service line from the interceptor to the main will be a minimum 6-inch diameter pipe and a manhole will be required at the point the 6-inch service ties into the city's sewer main.
Car Wash, Auto Painting or Repair Facilities
Car wash, auto painting or repair and chemical recycling facilities will be required by the City to have an outside interceptor in accordance with the Uniform Plumbing Code (WAC 51-56).
The location of the interceptor will be approved by the City Municipal Services Department for inspection access requirements.
City sewer will not be utilized by food services from a vehicle. Dumping of waste into city sewer manholes will not be allowed